Joven JH35 Water Heater East Meadow Replaced with Rheem EHG-30 30L Storage Water Heater at Condominium, 30 Tanah Merah Kechil Road, Tower 1A East Meadow November 1st, 2022
Replacement of an Joven JH35 Water Heater East Meadow at a Condominium, 30 Tanah Merah Kechil Road, Tower 1A East Medow unit.
Condominium, 30 Tanah Merah Kechil Road, Tower 1A East Medow
Replacement of a storage heater from existing Joven JH35 Water Heater East Meadow to resolve heater problems nd of service life.
Similar Rheem EHG-30 30L water heater is used for replacement. All pipe works connecting to the heaters are replaced with stainless steel. A new approved stop and double check valves are employed in accordance with the manufacturer’s specification. Such will comply with PUB.Our Licensed has supervised and approved the installation.There is a 1-year warranty by Homeone for this installation on top of the warranty provided by manufacturer.
The final result
Table of Contents
Old storage water heater: Joven JH35 Water Heater East Meadow above the false ceiling.
New storage water heater:Rheem EHG-30 30L Storage Water Heater, This heater unit has met the following requirements for a water heater:
The electric water heater as a whole unit (i.e. parts incorporated in the water heater itself such as heating element, pressure relief valve/temperature relief valve, water tank, etc. shall be tested in accordance with the following:
AS/NZS 4020:2018 Appendix K – Sample extraction procedure for use with water heating system. An accredited or non-accredited test report for Appendix K is acceptable provided that the test laboratory is accredited by Singapore Accreditation Council (SAC) to AS/NZS 4020:2018 Appendix H on Extraction of Metals, at the point of testing;
The samples extracted in accordance with Appendix K shall then be tested in accordance with AS/NZS 4020:2018 Appendix H – Extraction of metals (for metallic materials in contact with water). The maximum allowable concentrations of metals listed in Table 2 of AS/NZS 4020:2018 shall not exceed the limits specified by the World Health Organization (WHO) Guidelines for Drinking Water Quality.
All water service installations must be in accordance with the Public Utilities (Water Supply) Regulations, Singapore Standards 636 for Water Services and all other relevant statutory requirements.
The proposed works shall not adversely affect the existing water supply reticulation system.
Proposed water storage heater is installed in accordance with the specifications and requirements of the manufacturer. The installation of double check valves is safe and effective to prevent backflow and the back siphonage of water from the storage water heater through the heater inlet pipe and will be safe for use.